The Regulatory Reform (Fire Safety) Order (RRFSO) 2005, which came into force in October 2006, charges the responsible person in control of non-domestic premises and the common areas of a House in Multiple Occupancy (HMO) with the safety of everyone in the building, whether working, visiting or living there. This duty of care includes the provision of emergency lighting;
"Emergency routes and exits requiring illumination must be provided with emergency lighting of adequate intensity in the case of failure of their normal lighting".
Emergency lighting is part of the fire safety provision of a building;
"The legal requirement is that non-domestic buildings must be safe at all times, even if mains power failure occurs. Therefore, nearly all such buildings must have emergency lighting fitted".
No matter the size or complexity of requirement our experienced team has the knowledge to deliver efficient and effective emergency lighting system solutions that meet Regulatory requirements, ranging across all aspects of planning and design of the system, positioning of emergency lighting luminaires (wall / ceiling mounted lights and signs), periodic testing / maintenance of the system.
Types of systems are as follows, in both conventional and LED type fittings;
Maintained emergency luminaire: a luminaire in which the emergency lighting lamps are on at all times. Maintained mode is generally used in places of assembly such as theatres, cinemas, clubs and halls; the full list is contained in BS 5266. The lights are typically dimmed when these premises are occupied and the emergency escape lighting prevents total darkness.
Non-maintained emergency luminaire: a luminaire whose emergency lamps only come on when the power supply to the normal lighting fails. Non-maintained is the typical mode in a workplace or similar environment in which artificial lighting is normally deployed while the premises are occupied.
Combined emergency luminaire: a luminaire containing two or more lamps, at least one of which is energized from the emergency lighting supply and the other(s) from the normal lighting supply. A combined emergency luminaire can be either maintained or non-maintained.
Compound self-contained emergency luminaire: a luminaire providing maintained or non-maintained emergency lighting and also the emergency power supply to a satellite luminaire.
Satellite emergency luminaire: a luminaire for maintained or non-maintained operation and which derives its emergency operation supply from an associated compound self-contained emergency luminaire.